|Product Name:||Three Phase Contactless AVR Voltage Stabilizer||Product Model:||ZPW-20KVA|
|Input Voltage:||304~456V (could Be Customized)||Output Voltage:||380V/400V/420V/440V|
|Output Precision:||±1% ±2%||Reaction Time:||<30ms|
auto voltage stabilizer,
avr voltage regulator
Three Phase Contactless Avr Voltage Regulator 380V 20KVA With Black Enclosure
1. Product Introduction
Product name: three phase contactless AVR voltage stabilizer
Product model: ZPW-20KVA
Rated capacity: 20000VA
Rated working efficiency: 45-60Hz
Phase: three phase
Current type: AC
Input voltage: 304-456V or tailored according to your needs
Output voltage: 380V/400V/420V/440V or customized
Voltage regulating way: automatic regulation
Response time: less than 30ms
Display: LCD dispaly
Voltage stabilization precision: ±2% or ±1%
2. ZPW Series Specifications
customized according to real
|Input||Wires||3 wires + N|
|Voltage range||304 to 456V or customized|
|Output||Wires||3 wire + N + PE|
|Voltage||380V or customized|
|Response Time||Less than 30ms|
|Delay time||Five seconds|
|Waveform||No additional waveform distortion|
|LCD Display||Input voltage||
Real-time show of input voltage
and its fluctuation
Real-time show of the output
|Output current||Display of the working current|
The indication light on the LCD
screen would show the condition
of the stabilizer, like voltage
Less than 90%
|Altitude||Less than 1500m|
|Electrical Parameters||Electrical Strength||2000VAC/min, without flashover|
|Insulation Resistance||≥2 MΩ|
3. Protection Functions
① Over-load protection: when the actual load is higher than the rated capacity, stabilizer would power off automatically.
② Over-voltage protection: if the output voltage is 10% higher than the rated output voltage, the stabilizer stops working automatically.
③ Over-current protection: this protection function is the same as the first one, over-load protection. If the load is over rated one, the current would be higher than the rated one too.
④ Short-circuit protection: if there is a short circuit, the stabilizer would also cut off the power automatically to protect the electrical machine.
⑤ Time delay protection: there is a five-second time delay when the stabilizer powers on in order to protect the stabilizer itself.
4. More pictures
This picture shows the inner parts of the contactless AVR voltage stabilizer. Please have a look at the silicon-controlled modules and the circuit boards. These parts are very crucial to the stabilizer.
This picture mainly shows the other side, from which you could see the transformers which controls the output precision. Normally, there are six transformers for a stabilizer. Here, there are nine transformers, for which the precision of this stabilizer could be up to ±1%.